EPJ Web of Conferences
Volume 25, 2012EFM11 – Experimental Fluid Mechanics 2011
|Number of page(s)||16|
|Section||Experimental Fluid Mechanics 2011|
|Published online||16 April 2012|
Micro bubble formation and bubble dissolution in domestic wet central heating systems
Department of Mechanical Engineering, c/o Research
Office, School of Engineering and Design, Michael Sterling Building, Brunel
University, Uxbridge UB8 3PH, United Kingdom
2 Department of Mechanical Engineering, Room: H118, Brunel University, Uxbridge, UB8 3PH, United Kingdom
16 % of the carbon dioxide emissions in the UK are known to originate from wet domestic central heating systems. Contemporary systems make use of very efficient boilers known as condensing boilers that could result in efficiencies in the 90-100% range. However, research and development into the phenomenon of micro bubbles in such systems has been practically non-existent. In fact, such systems normally incorporate a passive deaerator that is installed as a ‘default’ feature with no real knowledge as to the micro bubble characteristics and their effect on such systems. High saturation ratios are known to occur due to the widespread use of untreated tap water in such systems and due to the inevitable leakage of air into the closed loop circulation system during the daily thermal cycling. The high temperatures at the boiler wall result in super saturation conditions which consequently lead to micro bubble nucleation and detachment, leading to bubbly two phase flow. Experiments have been done on a test rig incorporating a typical 19 kW domestic gas fired boiler to determine the expected saturation ratios and bubble production and dissolution rates in such systems.
© Owned by the authors, published by EDP Sciences, 2012
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.