EPJ Web Conf.
Volume 153, 2017ICRS-13 & RPSD-2016, 13th International Conference on Radiation Shielding & 19th Topical Meeting of the Radiation Protection and Shielding Division of the American Nuclear Society - 2016
|Number of page(s)||4|
|Section||5. Fission Facilities, Fuel Cycle & Waste Management Facilities, Decommissioning|
|Published online||25 September 2017|
Activation calculation for the dismantling and decommissioning of a light water reactor using MCNP™ with ADVANTG and ORIGEN-S
1 Wissenschaftlich-Technische Ingenieurberatung (WTI) GmbH, 52428 Jülich, Germany
2 EnBW Kernkraft GmbH, 76661 Philippsburg, Germany
a Corresponding author: email@example.com
Published online: 25 September 2017
The decommissioning of a light water reactor (LWR), which is licensed under § 7 of the German Atomic Energy Act, following the post-operational phase requires a comprehensive licensing procedure including in particular radiation protection aspects and possible impacts to the environment. Decommissioning includes essential changes in requirements for the systems and components and will mainly lead to the direct dismantling. In this context, neutron induced activation calculations for the structural components have to be carried out to predict activities in structures and to estimate future costs for conditioning and packaging. To avoid an overestimation of the radioactive inventory and to calculate the expenses for decommissioning as accurate as possible, modern state-of-the-art Monte-Carlo-Techniques (MCNP™) are applied and coupled with present-day activation and decay codes (ORIGEN-S). In this context ADVANTG is used as weight window generator for MCNP™ i. e. as variance reduction tool to speed up the calculation in deep penetration problems. In this paper the calculation procedure is described and the obtained results are presented with a validation along with measured activities and photon dose rates measured in the post-operational phase. The validation shows that the applied calculation procedure is suitable for the determination of the radioactive inventory of a nuclear power plant. Even the measured gamma dose rates in the post-operational phase at different positions in the reactor building agree within a factor of 2 to 3 with the calculation results. The obtained results are accurate and suitable to support effectively the decommissioning planning process.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.