EPJ Web Conf.
Volume 153, 2017ICRS-13 & RPSD-2016, 13th International Conference on Radiation Shielding & 19th Topical Meeting of the Radiation Protection and Shielding Division of the American Nuclear Society - 2016
|Number of page(s)||7|
|Section||5. Fission Facilities, Fuel Cycle & Waste Management Facilities, Decommissioning|
|Published online||25 September 2017|
Shielding analysis in the design phase of the new Emergency Operation Facility for Tihange Nuclear Power Plant
Radwaste management – Decommissioning – Radiation protection, Tractebel, Ariane avenue 7, B1200 Brussels – Belgium
* Corresponding author: email@example.com
Published online: 25 September 2017
In the framework of the design studies for a new Emergency Operation Facility (EOF) for Tihange NPP, radiation protection analyses are needed to comply with effective dose rate criteria. In this aim, the shielding performed by, at the one hand, external walls and roof of the building and, on the other hand, internal walls, has been sized by means of MicroShield calculations. This paper explains how the calculations for external walls, doors, roof, floor and internal walls are made. The assumptions on the source terms and on the source geometry as well as the way the shielding is determined and the results of the sizing are presented.
© The Authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.