EPJ Web Conf.
Volume 157, 201722 Topical Conference on Radio-Frequency Power in Plasmas
|Number of page(s)||4|
|Published online||23 October 2017|
Maintenance and preparation of the 3.7 GHz LHCD system for WEST operation
CEA, IRFM, F-13108 Saint Paul-lez-Durance, France.
* Corresponding author Email adress : firstname.lastname@example.org
Published online: 23 October 2017
The generator for the 3.7 GHz Lower Hybrid Current Drive (LHCD) system on Tore Supra consists of 16 klystrons capable of delivering 600kW/1000s each on plasma. Such a powerful installation needs to be operated on a regular basis in order to preserve the specifications of the klystrons in terms of output power and pulse duration. This has been of particular importance during the long shutdown between the last Tore Supra campaign in 2011  and the start of LHCD experiments on WEST in 2017. The TH2103C klystrons have been operated on matched load once a year during the shutdown. A reduction of 14% of the available RF power for the experimental program is found, which is partly due to the loss of one klystron. Another important aspect of the maintenance procedure is to maintain the knowledge of the operating team at a good level. This paper describes the procedure and tests performed during six years of shut-down. It also summarizes the technical problems encountered and the consequences on the test schedule, and highlights the importance of maintaining such large plants in operating condition during shutdowns.
Key words: klystron / Lower Hybrid / RF heating system / generator
© The authors, published by EDP Sciences, 2017
This is an Open Access article distributed under the terms of the Creative Commons Attribution License 4.0, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.